CNG Compressor – Ingersoll Rand 20H40NGDX
P.C. McKenzie Company has served the CNG Compressor industry for over 25 years. During that time we have built small CNG Compressors that fill vehicles and forklifts, to the larger units that fuel transport buses for the US Army.
Our CNG Compressors are manufactured and built right in the USA with known and trusted brands such as Ingersoll Rand and Sauer Compressor.
From the largest CNG Compressor rated 210 scf to the smallest compressor rated 28 scf, our compressors; our units are built to last with an emphasis on low maintenance.
Take A Look at The CNG Compressors Sizes We Have To Offer:
Larger CNG Compressor –
Call us For More Information on larger compressors.
Model – 05WP4341-SX – 46 scfm
Model – 05WP4341-DX – 92 scfm
Model – 05WP4351-SX – 104 scfm
Model – 05WP4351-DX – 204 scfm
Ingersoll Rand CNG Compressor –
Find Out More Information Here >> Ingeroll Rand Natural Gas Compressor
05H25NGSX- 28 sfcm
05H25NGDX- 56 sfcm
Please contact us for natural gas compressors in any of the above size ranges or larger. We are here to help you achieve the best results in your CNG Refueling Stations. We have many years of experience sizing CNG Compressors for you needs.
Ingersoll Rand CNG Compressor
How To Size A CNG Compressor Station
There are some key pieces of information needed to properly size an NGV refueling station. As with any project, the more information you provide; the more accurate an estimate can be given.
Here are some key questions to consider as you move forward.
Determine what type of vehicles will be refueled. Light duty vehicles? Forklifts? School Buses? Municipal Vehicles?
The type of vehicles you plan to fill will help us determine the best station design for your specific fleet. For example, if you have a school bus fleet you will probably refuel these in a different manner than say a taxi fleet based upon the vehicle operating times.
How many vehicles will be refueling at this site?
This is a critical piece of information since this will help determine the station loading or how much natural gas must be delivered.
Determine the amount of gasoline each vehicle requires.
Again, another crucial piece of information needed. We use a conversion factor of 125 scf per equivalent gallon of gasoline. So, if you have a pick-up truck that takes 10 gallons of gasoline every day we know that it will require 1,250 scf of natural gas every time it fills up. Try to get as accurate a number as you can since this will again determine station load.
What time frame will the vehicles refuel in?
Sizing an NGV refueling station is like sizing a water heater for your home. If you have a lot of children taking showers before they leave for school in the morning you will need a large storage tank.
NGV refueling stations are sized based upon how many vehicles will fuel, how much fuel they will take and in what time frame. Will all the vehicles arrive early in the morning to fuel? Will 2 or 3 vehicles fuel every 3 hours or will they all fill over night?
Determine if the vehicles need to be fast filled or if they can be time filled.
This further defines the amount of time available to fuel the fleet. For example school bus fleets typically are refueled over an 8 hour period during the evening. If they were to be fast filled in the morning before they go out on their routes, the NGV refueling station would have a much different design.
Will the amount of CNG transferred into each vehicle be accounted for?
In some instances, fleet managers need to know how much fuel is used in each individual vehicle. In other case, like school bus fleets, they only need to know the total amount of fuel used by the entire fleet. If each vehicle must be accounted for a dispenser will be needed along with a card lock system to assign the amount of fuel transferred to a particular vehicle. This is an important point since it will impact the overall cost of a station.
Will the station be used for a private fleet or for public refueling?
This ties into accounting for individual vehicle accountability. Certainly in a public refueling station you will need to know how much fuel is transferred in order to bill the customer.
Will the station demand grow in the future and, if so, by how much?
We have found many customers that wish to start with a portion of their fleet and then, as they prove the benefits of natural gas, add more NGVs. If this is the case, it helps to know from the beginning of the project. The number and size of conduit can be sized accordingly along with the addition of compression modules and/or storage.
What utilities are available at the location that you wish to install your station?
We will need to know what the available gas pressure is at the site and what the gas quality. This can be secured from your local gas utility. Of particular interest is the moisture content of the gas. All natural gas contains a certain amount of water. Pipeline quality gas is measured at 7#/MMSCF, this means 7 pounds of water in 1,000,000 cubic feet of natural gas. This works fine for the burner tip but might be a problem for NGV refueling, so we will need to know this amount in order to properly size an inlet dryer.
We will also need to know what electrical service is available at the site. Ingersoll Rand CNG packages use 460V/3Phase power. If 208Volt is available, we will need to know this to provide the correct motor.
At what pressure will your vehicles operate?
Typically, NGVs store gas onboard at 3,600 psi. Older vehicles had operated at 3,000 psi but we find this to be a rare occurrence. Confirm what fill pressure is required.
Once you have gathered all of the above information contact P. C. McKenzie Company to discuss your particular application. We can size your station based upon your unique requirements and offer suggestions to improve performance or reduce station costs.
CNG PRE-CONSTRUCTION CONSIDERATIONS
Secure and review the current NFPA-52 guidelines for Compressed Natural Gas Vehicular Fuel Systems Code. This code is published by the National Fire Prevention Association and applies to all the design and installation requirements of CNG refueling facilities.
Contact your local Fire Marshall and Building Inspector who can help guide you through local code requirements and the permitting process.
Contact your natural gas provider to determine:
a) Gas pressure available at your location
b) Gas quality including moisture content
c) That the existing gas service can support the gas flow required by the station
Contact your electric company to determine:
a) Electrical service available at the site
b) Can the existing service support the electrical demand for the station
Contact a local contractor that is qualified to install an NGV Refueling Station.
P.C. McKenzie Company has many contacts throughout the USA to help with providing station installation.
Contact Us Today for Help in Sizing Your CNG Compressor Station!