A Check List for Planned Preventive
P. C. McKenzie Company offers planned preventive
maintenance services for a number of industrial and commercial boiler
installations. Although each installation is unique there are some common
maintenance steps that our service group follows.
Even though not all of these steps apply to every boiler
design, we thought they might prove helpful in designing a planned preventive
maintenance check list for your facility.
front and rear doors. Clean and vacuum fireside surfaces as required.
all refractory. Patch and wash coat as required.
all gasketing on front and rear doors and replace as necessary.
and close front and rear doors properly.
low and auxiliary low water cut off controls, clean and inspect. Then
re-install using new gaskets.
plugs in control piping, inspect, clean and re-install.
all hand hole and man hole plates. Flush boiler with water to remove loose
scaled and sediment.
all hand hole and man hole plates with new gaskets.
feedwater tank manway, inspect and clean as required. Replace manway plate
with new gasket.
burner and burner pilot.
pilot electrode and adjust or replace.
air damper and blower assembly.
motor starter contacts and check operation.
necessary adjustments to burner for proper combustion and record all results
in service report.
all flame safeguard and safety trip checks and record results in service
all hand hole plates and man hole plates for leaks at normal operating
temperatures and pressures.
any boiler system problems as requested by on-site personnel.
Our Boiler Parts Department
55 + years of experience - we
are the experts when it comes to finding those "hard to find" parts. We
can help you with your boiler questions and put together a
maintenance kit for your boiler ... call toll free for more
info - 877-244-4883!